Description of function
Manual Leak Check LPG PRO BT - App Operation
The manual contains all important tips for operating the Leak Check LPG PRO BT in combination with the corresponding app.
From setup and app settings to the final check, you will find everything you need to know in the manual.
Function test of anti-siphoning devices
These days, mechanical or electromagnetic anti-siphoning devices in oil firing installations are state of the art. However, no recurring function test has yet become established.
The general building-authority approvals specify a function test of anti-siphoning devices every 5 years.
Safe shut-off function of an excess flow device
In order to guarantee the shut-off function of an excess flow device, maximum lengths of hose assemblies must be respected.
The admitted lengths of hose assemblies depending on flow, nominal pressure and dimensions can be seen in the corresponding charts.